Notice: Undefined variable: adsns_count in /home/systemte/public_html/electrical/wp-content/plugins/adsense-plugin/adsense-plugin.php on line 346
Chapter 52 Selection and erection of wiring systems
Regulation 521.11.201 which give requirements for the methods of support of wiring systems in escape routes, has been replaced by a new Regulation 521.10.202. This is a significant change.
Regulation 521.10.202 requires cables to be adequately supported against their premature collapse in the event of a fire. This applies throughout the installation and not just in escape routes.
Regulation 522.8.10 concerning buried cables has been modified to include an exception for SELV cables.
Regulation 527.1.3 has also been modified, and a note added stating that cables also need to satisfy the requirements of the CPR in respect of their reaction to fire.